Replacing water meter
Installation of water meter is a plumber. This assembly is normally performed at the moment of putting into operation a new home. It must be remembered that after sealing the counter, you can not carry out any repairs yourself, because we can be accused of is that we were trying to cheat on the amount of water consumed by us, thus reducing the incoming letter bills. Such a meter reading is a worker employed by a company supplying us water. But reading the meter of water is so simple that we can also ourselves through his regular reading to control the amount of water consumed by us. Sometimes it may happen that the water meter sours after many years of its use. Replacement of such counter will plumber.
Gaskets - what are they?
Gaskets are mechanical seals, usually formed like a ring and used for sealing of flange joints. In general, gaskets should not be reused. Various types of gaskets are available depending upon their construction, materials, and features. The following are the type of gaskets commonly used:
Non-Metallic Gaskets (ASME B 16.21)
Spiral-Wound Gaskets (ASME B 16.20)
Ring Joint Gaskets (ASME B 16.20)
Non-Metallic Gaskets are used with flat face or raised face flanges. Spiral-Wound Gaskets are used with raised face flanges. They are available with an inner ring and outer ring, which is also known as the cantering ring. Ring Joint Gaskets are used with Ring Type Joint (RTJ) flanges. They are available in octagonal or oval cross sections.
A very high surface stress is developed between an RTJ gasket and the flange groove when RTJ is bolted up in a flange. This leads to plastic deformation of the gasket. Thus, the hardness of the gasket is kept less than the hardness of the groove to achieve coining i.e. bringing two metal surfaces of different hardness so tightly together that the softer surface deforms to match harder surface exactly in shape and finish. Hence RTJ gaskets are not recommended for reuse.
Galvanized pipes for plumbing - what are they?
Galvanized steel potable water supply and distribution pipes are commonly found with nominal pipe sizes from 3?8 inch (9.5 mm) to 2 inches (51 mm). It is rarely used today for new construction residential plumbing. Steel pipe has National Pipe Thread (NPT) standard tapered male threads, which connect with female tapered threads on elbows, tees, couplers, valves, and other fittings. Galvanized steel (often known simply as "galv" or "iron" in the plumbing trade) is relatively expensive, and difficult to work with due to weight and requirement of a pipe threader. It remains in common use for repair of existing "galv" systems and to satisfy building code non-combustibility requirements typically found in hotels, apartment buildings and other commercial applications. It is also extremely durable and resistant to mechanical abuse. Black lacquered steel pipe is the most widely used pipe material for fire sprinklers and natural gas.
Most typical single family home systems won't require supply piping larger than 3?4 inch (19 mm) due to expense as well as steel piping's tendency to become obstructed from internal rusting and mineral deposits forming on the inside of the pipe over time once the internal galvanizing zinc coating has degraded. In potable water distribution service, galvanized steel pipe has a service life of about 30 to 50 years, although it is not uncommon for it to be less in geographic areas with corrosive water contaminants.